|Water conditioning can be described as "virtually any form of
water treatment designed to improve the aesthetic quality of water by
the neutralization, inhibition or removal of undesirable substances".
Traditionally, various types of water treatment equipment have most often employed
chemical interactions to obtain a predetermined result. Chemical
reactions are quite well understood, and the outcome is typically very
predictable. The problem with chemical water treatment is usually
that there are some, if not many, negative side effects to take into consideration.
The negative side effects can often outweigh the positive results
achieved, from an environmental point of view.
Physical water conditioning does not incur the negative side effects
associated with most chemical treatments. The problem with
physical water treatment has historically been dependability and
consistency of the treatment.
Because so little is actually understood about physical interactions,
most PWT vendors have been unable to properly specify their products for
various applications. If a manufacturer (or distributor) doesn't fully understand
the principles and dynamics of a system, how is it possible to properly
specify a solution? Most of the time it has been a "try and see if
it works" approach for these types of products. The majority of
these products are various types of magnets, electric coils, etc.
Most all of these have had a limited success ratio for this
HydroFLOW is a physical water conditioner which eliminates the problems
associated with proper specification of correct units for specific water
conditioning applications. Specification has been inherently
incorporated into the unit design by correctly sizing the power output
and signal dynamics of the units for each specific application the unit
is intended for.
With a HydroFLOW unit being properly installed, success is assured.
As for "proper installation", there can be a little more to it than
first meets the eye. This is why we typically like to work closely
with our clients to insure a proper installation. Location is
key. In each application, there are good locations, and bad
locations. Then, there is what you might call "the sweet spot"
where the water conditioning unit will operate at maximum efficiency.
Because the Hydropath unit is ELECTRICAL in nature (not
magnetic), one must think of the plumbing system as an
electrical circuit. The best location for maximum efficiency
would be somewhere near the "center" of the system, because the signal
is propagated both upstream and downstream of the unit itself.
Because an electrical signal divides at each branch of the plumbing
system, (the actual voltage divide is determined by the impedance of
each branch) some thought must go into placement for best results, even
though the unit might actually work perfectly well placed in many
various locations within the system. Problems arise when the
unit is placed in what can be considered an electrical loop.
When placed in a loop, the signal is unable to propagate throughout the
system, but instead circles around a small sub-section of the plumbing
system. If placed in a loop, failure is assured.
Loops can often times be not so obvious to the eye. Keep in mind
that when we are speaking of loops, we can be referring to either:
- The plumbing
system itself (the conductive path of the fluid) or:
- In cases with
conductive piping such as copper, the associated piping and mounting
components. (various conductive hardware)
In the case of hardware loops, this can be caused
by the brackets, pipe hangers, grounding straps, etc., attached to a
metallic pipe. A good example of a hardware type loop would be
a case of metal piping supported
with metal hangers, suspended from a metal beam. Referring to diagram 1 below,
the red line indicates the low-impedance path the signal will take which
creates a loop around the unit.
Note: If a beam (or rebar) is a part of a concrete
inner-structure, you may not even be aware that it is
there creating the loop.
A good example of a fluid system loop would be if the unit is placed within
a parallel section of a pumping & filtration system. Referring to diagram 2
below, the red line indicates the low-impedance path the signal will
take which creates a loop around the unit. Notice that the signal
strength may be diminished by the pump and filter components, however
the loop will create an undesired condition. It can be
considered the same as if the pumps and filters were not in the system.
This type of loop is much more evident, and should be easily observed by
looking at the piping configuration itself. This same type of loop
can occur if the unit is placed near a meter which has a bypass loop,
even when the valves are closed. (the signal will
pass straight through metallic valves!)
Note: Either of the above two examples could be
easily corrected by properly placing the Hydropath unit upstream
of the loop.
The unit could also be placed downstream of the
loop in the case of Diagram 1, if it is determined to be a better
As you can see, we MUST avoid loops in any case when installing
As long as the unit is not placed within a loop, some level of success is
assured. Best placement can only be achieved through a
comprehensive review of the entire system to be treated. When we
work with our clients for treating specific applications, they can
always be assured that the Hydropath units will be properly installed
for maximum results.
If the units are to be installed yourself, please be
willing to allow us to provide advice and assistance for proper
placement. This may involve sending us photographs of the
installation, and close communication with us to ensure a successful